Current Region: Global (EN)
This site uses some unobtrusive cookies to store information on your computer. By using the website, you hereby agree on cookies storage.
How can we help you?
IIn order to make the water drinkable, the Dosatron ACS or NSF certified metering pumps, installed in line with the water pipe, inject a dose of chlorine (NaClo, CaClo) which allows the destruction of organic matter such as viruses and microbes contained in the water, in proportion to the flow rate.
Since a large part of the chlorine is needed to neutralize these organic materials, the dose of chlorine delivered by the metering pump will allow a part, called free residual chlorine, to remain available to treat possible future contamination of the water in the network or in the homes.
According to the WHO, in drinking water treatment, the free chlorine concentration of the treated water should be 0.2 to 0.5 mg/l.
Dosatron chlorine dosing pumps certified by the ACS comply with the quality requirements set out in the French Public Health Code (CSP) transposing Directive 98/83/EC of 3 November 1998 on the quality of water intended for human consumption.
The validity of a certificate can be verified by contacting the issuing laboratory, or by consulting the list of valid health certificates of conformity published by the Carso Group laboratories.
The D8WL range of chlorine dosing pumps meets dosing requirements for flow rates from 500 to 8,000 l/h (maximum flow).
The D8WL ACS chlorine dosing pumps have also obtained the mandatory French approval (ACS) for all equipment in contact with water intended for human consumption. See more
These chlorine dosing pumps are characterized by:
Installed on the water network, our metering pump uses water pressure as its sole driving force. Thus actuated, it sucks up the concentrated product, doses it at the desired percentage, then mixes it with the driving water.
The resulting solution is then sent downstream. The dose of product injected is always proportional to the volume of water flowing through our metering pump, regardless of variations in flow rate or network pressure.
In this installation, the injection pump is installed in by-pass in order to facilitate the maintenance of the pump without having to cut off the main water supply.
Be careful in this case the water will not be chlorinated anymore
This configuration also allows, if necessary, and if the main water flow is constant, to carry out a partial by-pass which allows only a part of the flow to go through the metering pump.
Upstream of the chemical dosing pump, on the main pipe, a 60 micron filter is installed to protect the dosing pump motor against impurities. After the filter, it is suggested to install a pressure reducer in order to be sure not to exceed the nominal pressure of the pump.
On the pipe, two taps are made, one before the dosing unit which will be used for the preparation of the mother solution. The other tap downstream of the dispenser can be used for testing the dispenser and/or priming it during start-up, during operation, for taking samples and finally, during maintenance, for rinsing the dispenser.
Finally, a non-return valve is required at the end of the dosing line to prevent water from flowing back into the dosing unit, which could in some cases return to the mother solution and dilute it or even cause the container to overflow.
During the installation, the dosing unit must be at a height higher than the mother solution and ideally not above but on the side.
The new smartphone application from Dosatron will allow you to perform all your chlorination calculations and share them with anyone you want.
Water-powered proportional dosing pumps manufacturer since 1974. DOSATRON provides you with quality fluid handling equipment, service excellence, a high level of expertise, and customer proximity all over the world.
Rue Pascal33370 Tresses - FRANCE | +33 05 57 97 11 11